50, when arranged inside the boiler room to note a safety distance, the front end of the boiler ready spacing of not less than 2/3 of the length of the furnace, and not less than 2 m; vertical boiler can be shortened; bulk boiler is not less than 4 m and does not affect the blast furnace operation and maintenance. 2, the boiler side and rear channel spacing of not less than 0.8 m, and should meet the operational and maintenance (such as replacement tube bundle cleaning, stirring the fire, etc.) requirements. 3, the top horizontal boiler headroom not less than 2 m; vertical boiler top clearance height to facilitate the operation and maintenance; headroom boiler room the other channels, should not be less than 2 meters, when the passage of time and no need to operate its headroom height of 0.7 meters. 4, the boiler room is provided for two or more boilers, the boiler the distance between adjacent not less than 1 to 1.5 times the cylinder diameter of the boiler. 5, the boiler room is generally preferred fireman operation chamber provided, on the total rated greater than or equal evaporation 4t / h steam boiler (heating or vertical oil firedfiredhot water boiler is equal to or greater than 2.8MW) must be provided stoker operating room. Electric boiler tank may be provided in front of the boiler, and to ensure the art to fireman facing boiler water gauge, pressure gauge and other instruments during operation. 6, to the total rated evaporation 2t / h fuel gas boiler room to be provided or water spray foam fire extinguisher system, should outdoor outdoor fire hydrant, other fire-fighting equipment should also have the boiler room. 7, the fuel in the boiler room daily oil tank, the oil pump is generally not located in the boiler room, between daily oil tank, the oil pump between the application of the fire resistance of greater than 2.00h wall, the fire resistance of greater than 1.50h floor spaced from the other parts. Daily fuel tank between the boiler room and the door between the oil pump should be able to self-closing fire doors Class A, and let the oil block measures. Household upper tank return pipe to be provided, should be greater than the oil return pipe back to the oil pump. 8, an oil tank and all piping must have a reliable electrostatic grounding, the grounding resistance should not exceed 30 ohms. 9, gas boiler room boiler design should also comply with the relevant safety requirements of gas boiler room.
ASME is referred to as "the American Society of Mechanical Engineers", mainly dedicated to the development of machinery industry standards, and was recognized by most countries in the world. Get ASME certification is fast boiler and pressure vessel products to the international market, the only way to obtain a certificate issued by ASME and stamp means getting the products exported to international market, "pass."
Pressure fuel boilers interpretation of the overall daily operation and maintenance of oil-fired boilers with atmospheric corrosion knowledge structure, including boiler and auxiliary equipment of two parts. Boiler furnace, drum, burner, water wall superheater, economizer, air preheater, and the furnace wall, etc. The main frame member constituting the core part of the steam production, called boiler. Boiler body is in two main parts and drum furnace. Also known as the furnace combustion chamber, fuel combustion for space. The solid fuel on to the grate, referred to as a fire bed combustion furnace Stoker, also known as fire bed furnace; solid fuel furnace liquid, gas or pulverized, is injected into the combustion chamber is called the fire chamber burner, also known as the furnace fire chamber; air coal particles burn hold it was boiling, and the furnace is inferior fuel suitable for combustion is called fluidized bed furnace, also called fluidized bed furnace; coal particles so that an air flow rotated at high speed, and strongly called fire cylindrical cyclone furnace hearth. Boiler pressure fuel daily operation and maintenance link and chemical corrosion, turbine attendant prepare enough desalinated water, oxygen, water passing temperature no higher than the drum wall temperature 50 ℃; Sheung during hot drum wall temperature should be after the temperature of the metal is not more than 40 ℃ before a new installation or repair departments boiler Feed records an indication of expansion. Sheung summer time less than 2 hours, at least 4 hours in winter, when the temperature and Sheung drum wall temperature difference of less than 40 how ℃ boiler reheater corrosion protection? after turbine fight gate, boiler guarantee a blower, an induced draft fan is running the best cross retain two oil gun. turn reheaters to the empty exhaust steam reheater hydrophobic doors and air doors corrosion, anti-corrosion of the reheater steam temperature is lower than a predetermined deg.] C for 400 control drum water level within an allowable range. anticorrosive time less than 20 minutes after stopping two oil gun operation. guarantee furnace pressure when 50--100Pa, each of the flaps open, baffle for ventilation less than 5 minutes, stop sending, fan, each of the flaps closed tailgate may be appropriate to accelerate Sheung speed.
Gas-fired steam boilers are a very wide range of special equipment, usually built in boiler rooms. However, in the process of loading and installation, some problems must be paid attention to, otherwise it may cause a certain degree of economic loss.
1. Pay attention to the following matters during the loading and unloading and handling of gas-fired boilers: the lifting capacity of the lifting equipment should match the weight of the lifting boiler. The lifting lug on the boiler with the lifting lugs that cannot be used for lifting can not be used for lifting. The length of the steel cord should be reasonably selected to avoid the scratching of the furnace due to the improper length of the steel cord. The boiler must be protected from any damage during handling and handling.
2. Reserves for maintenance space When installing boilers, ensure that there is sufficient maintenance space around the boiler.
3. Setting and precautions for the base and base of the gas steam boiler The boiler body must be installed on the basis of 100-150mm above the floor of the boiler room. It must be confirmed with the technical personnel of the boiler manufacturing company in advance and constructed according to the basic drawings. The anchor bolts must be reserved on the foundation. The foundation shall be capable of withstanding the maximum weight of the boiler and the amount of water it holds. When installing the base, you must first position it. After positioning, adjust to the same length of the two diagonals of the base, and then tighten all the fixing bolts. The installation of the base is carried out with reference to the reference line.
4, general precautions Be careful not to tilt and impact the boiler and accessories too much. No combustibles can be placed around the boiler. Do not use oil and water to smother the boiler. The boiler should normally be installed in a separate boiler room. The new gas-fired boiler room should not be connected to the house. The boiler room shall not be connected to Class A, Class B and Category C fire hazard rooms using flammable liquids. If connected to other production plants, the application firewall is separated.
Vertical Gas & Oil Fired Hot Water Boilers | Reliable Oil & Gas fired hot water boiler is widely used in factory, school, hotel, restaurant, hospital, residence community, bath center, indoor pool. Advantage Feature of Oil & Gas Fired Hot Water Boilers Compact Structure: Vertical boiler occupies small space, light weight, intelligent control.Learn More
2011-7-26 · Vertical Oil Gas Fired Hot Water Boiler - EPCB Products Made In China, China Manufacturer. Vertical oil(gas) Fired fire tube Hot water boiler LNS series of oil gas fired hot water boiler is fire tube and vertical type boiler, and is the new patented technology boiler which developed independently by . Get a QuoteLearn More
Vertical oil(gas) Fired fire tube Hot water boiler LNS series of oil gas fired hot water boiler is fire tube and vertical type boiler, and is the new patented technology boiler which developed independently byLearn More
vertical oil-fired hot water boiler for hotel. 700Kw Gas Vertical hot water boiler used for hotel, 700Kw Gas Vertical hot water boiler used for hotel, school Introduction. Introduction The biomass horizontal steam boiler is a horizontal three-return water-fired tube hybrid boiler in which a bundle of threaded tobacco pipes is arranged.Learn More
Apr 23, 2019 · The series boiler is vertical industrial water tube oil fired steam boiler. steam capacity is 0.1-2t/h. thermal efficiency is 92%. Biomass Fired Thermal Oil Boilers The 360,0000Kcal biomass fired thermal oil heater use for plywood plant in Indonesia. thermal efficiency is 80%.Learn More
Vertical Oil Fired Gas Fired Hot Water Boiler For Hotel Oil Fired Boiler, China Oil Fired Boiler Suppliers China Oil Fired Boiler, Oil Fired Boiler from China Supplier - Find Variety Oil Fired Boiler from coal fired boiler,waste oil boiler,thermal oil boiler, Boilers Suppliers Located in China, Buy Oil Fired Boiler Made in China on Alibaba.comLearn More
Fangkuai boiler manufacturers provide 0.5-1 tons of vertical hot water boilers, which can be jointly controlled to meet the demand for hot water in shopping malls, hotels, schools and other places.Learn More
Rental services for products such as boilers including gas fired, & hot water vertical boilers, waste oil, vulcanizing, sectional, range, & field erected boilers. Power range of 30 HP - 250,000 HP, & wide range of maximum pressure. Auxillary equipment such as DAs, water softeners, feedwater systems, heat exchangers, & economizers is also available.Learn More
CLHS Vertical Oil (gas) Hot Water Boiler, find complete details about CLHS Vertical Oil (gas) Hot Water Boiler, oil/gas fired hot water boiler, hot water boiler price, Vertical Oil (gas) Hot Water Boiler - Wilford Thermal-innovative leader of Boiler science&technologyLearn More
Buderus has a full product line including condensing boilers, wall-hung boilers, residential gas-fired boilers, residential oil-fired boilers, commercial boilers, domestic hot water storage tanks, climate and energy controls, panel radiators, solar heating systems and other hot water heating accessories.Learn More
China Vertical Oil Fired Boiler manufacturers - Select 2019 high quality Vertical Oil Fired Boiler products in best price from certified Chinese Boiler manufacturers, Industry Boiler suppliers, wholesalers and factory on Made-in-China.comLearn More
CLHS vertical type Oil and Gas Fired Hot Water Boiler with CLHS oil and gas fired hot water boiler is vertical fire tube chamber consumption structure, which is suitable for gas or liquid fuel. As this series hot water boiler is working with normal pressure, there is no threaten of explosion, and it can be placed anywhere.Learn More
Oil/Gas Fired Boilers. Savemax Oil/Gas Fired Boilers are the basic 3 pass internal furnace smoke tube type design in which flue gases are inside the tubes while water is outside the tubes in the shell. The combustion of oil and gas in a furnace requires atomization of the fuel.Learn More
Vertical Hot Water Boiler Large water volume; precise temperature control system; food-grade enamel coating In order to satisfy commercial customers the demand of the volume-type small and medium sized hot water boiler, Fangkuai quickly introduced a gas-fired hot water heater with advanced condensing technology.Learn More
vertical oil firedgas firedhot water boiler 2011-7-26 · Vertical Oil Gas Fired Hot Water Boiler - EPCB Products Made In China, China Manufacturer. Vertical oil(gas) Fired fire tube Hot water boiler LNS series of oil gas fired hot water boiler is fire tube and vertical type boiler, and is the new patented technology boiler which developed independently byLearn More